BRASS, FULL BORE GATE VALVE, FXF, PN16rastelli2021-03-29T09:27:15+00:00
BRASS GATE VALVE PN16 FxF
BRASS GATE VALVE PN16 FxF FULL BORE
Brass full bore gate valve normal type. It can be used in a wide variety of sectors: heating, air conditioning, irrigation and sanitary systems and generally with any non- corrosive liquid. Gate valves can be horizontally or vertically installed. The slow and proportional manoeuvre avoid the water hammer phenomenon.
Pay attention during the installation phase, especially for the small size ones, avoid forcing the pipe screwing in order not to deform the sealing seats.
Gate valves can also work at an intermediate position of the opening, so as to reduce the flow into pipes.
Thread ISO228/1: FxF
Maximum working temperature: 80°C in absence of steam.
215: With steel handwheel
15S: With aluminium handwheel
THREADED BRASS GATE VALVES – Art 215: Full bore brass gate valve, FXF, PN16, steel handwheelrastelli2022-05-25T07:30:05+00:00
HOW TO INSTALL
Unpack the valve and check that the flow paths and valve threads are clean and free from debris. Check the body markings to ensure that the correct valve has been selected for installation. Rastelli gate valves are manufactured to exacting standards and, therefore, should not be subjected to misuse. The following should be avoided:
• Careless handling of the valve (Valves should not be lifted using the hand wheel, lever or the stem).
• Dirt and debris entering the valve through the end ports.
• Excessive force during assembly and hand wheel operation.
Confirm that the pipe threading length is correct to avoid excessive penetration of the pipe into the valve that would otherwise cause damage. Care should be taken to apply jointing compound to the pipe only and not in the valve threads. Surplus compound will then be forced outwards and will not enter the valve. Over use of compound can lead to valve failure on the body ends. Threads should be engaged correctly when tightening the valve onto the pipe. The wrench should always be fitted on the body end adjacent to the joint being made. Severe damage can occur to stems, valves and seats by the use of hand wheels larger than those originally supplied by the manufacturer, and by wheel keys.
No aesthetic care is required for this product.
A regular maintenance program is the most efficient method to ensure a long term efficiency of your gate valve. The program should include a risk assessment and a planned procedure of how the maintenance will be carried out.
The correct fitting tools and equipment should be used for valve maintenance. Separate means of draining the pipe work must be provided when carrying out any maintenance to valves. Where there may be any system debris this could be collected and/or filtered by installation of the appropriate protective device (see our items 411-412).
Necessary cookies are absolutely essential for the website to function properly. This category only includes cookies that ensures basic functionalities and security features of the website. These cookies do not store any personal information.
Any cookies that may not be particularly necessary for the website to function and is used specifically to collect user personal data via analytics, ads, other embedded contents are termed as non-necessary cookies. It is mandatory to procure user consent prior to running these cookies on your website.