Handle with care. Do not weld the flanges to the piping after installing the valve.
Water hammers might cause damage and ruptures. Inclination, twisting and misalignments of theU piping may subject the valve to stress, once installed. It is recommended that elastic joints be used in order to reduce these effects as much as possible. The disc must be partially open. The stem has a machined notch which indicates the position of the disc; consider this indication, in order to mount the levers and actuators correctly. The mounting can be made with the stem axis in a horizontal or vertical position. In case the fluid contains suspended solid particles (for example, sand, impurities, etc.) or solid particles that may leave deposits, it is recommend that the valve be installed with its axis horizontal, and in such a way that the bottom end of the disc opens in the direction of flow.
This item allows the dismantling of the pipes downstream, for pressures below 6 bar.
Verify maximum working pressure and limits of use. Place the valve between two flanges. While placing the valve, ensure there is sufficient space in order not to damage the rubber. Do not mountr seals between valve and flanges.
Carefully clean the contact surface. Do not install the butterfly valve in direct contact with a rubber surface (for example, expansion joints); the best installation is when the rubber is in contact with metal. Do not weld the flanges to the tube if the valve has already been installed.
Do not let protrusions or sharp edges on the piping cause damage to the rubber surface of the valve. Centre the valve on holes while using wafer type valves. Tighten the bolts crosswise and progressively, in order to distribute the pressure equally before the body and flanges come into contact with each other.
Turbulences of the fluid might increase erosion and reduce the life-cycle of the valve. Install the valve at a distance of at least 1 x DN upstream, and at a distance of 2-3 x DN downstream, away from fittings or bends. In the open position, the valve is larger than the nominal Face to Face value. Check that no other components of the piping interfere or create damage or malfunction. If they do, a spacer should be inserted for the valve to operate correctly.
For valve operating with hazardous liquids(toxic, corrosive…) , if there is a possibility of residue remaining in the valve, take due safety precaution and carry out required cleaning operation. Personnel in charge must be trained and equipped with appropriate protection devices.
Prior to disposal, disassemble the valve and separate the component according to various materials.
Please refer to product literature for more information. Forward sorted material to recycling (e.g. metallic materials) or dispose it, according to local and currently valid legislation taking into consideration the environment.
Necessary cookies are absolutely essential for the website to function properly. This category only includes cookies that ensures basic functionalities and security features of the website. These cookies do not store any personal information.
Any cookies that may not be particularly necessary for the website to function and is used specifically to collect user personal data via analytics, ads, other embedded contents are termed as non-necessary cookies. It is mandatory to procure user consent prior to running these cookies on your website.